KeLing Purification Technology Company Limited
Advanced. High-Qulity. Reasonable.
Payment & Shipping Terms:
|Style:||Plate And Frame||Place Of Origin:||GuangZhou, ShenZheng|
|Carbon Content:||12.3kg||Smell Rid Rate:||>95%|
hepa high efficiency particulate air filter,
clean room air filter
Activated carbon is a multi-aperture charcoal with pore structure and adsorption characteristics. Its adsorption is formed by physical and chemical absorption. Its appearance is black. Columnar activated carbon is used for purification of toxic gases, exhaust gas treatment. , industrial and domestic water purification treatment, also used to remove air pollutants and classified gas purification.
Our company acceptable non-standard order.The following are some of the other types of activated carbon filter products of our company.
Dimension And Parameter
Customer size is available.
|Standard sizes(W*H*D)(mm)||Primary Resistance(Pa)||Rated air volume(m3/h)||Filtration efficiency|
1. Activated carbon filter has strong surface adsorption capacity, which can effectively control odor and organic pollution in the air and solve the problem of air filtration in general air-conditioning and ventilation places.
2. Easy installation and maintenance, light weight, strong versatility.
3. The outer frame can be separated from galvanized frame, aluminium alloy frame, plastic frame or stainless steel frame. The structure is firm, the filter material can be easily replaced and reused.
4. With the filling structure, the effective air filtration area is greatly increased, the adsorption capacity is strong, and the resistance is low.
5.It can reduce toxic and harmful substances in exhaust gas and purify air. It is an efficient cleaning device to improve the life of purification system.
1.Rational use of activated carbon air filter.
2.The time that air passes through the activated carbon layer is generally greater than 0.1 second.
3.The dust and droplets in the air should be removed in advance.
4.Install a dust filter at the rear to prevent possible carbon contamination of the ventilation system .
5.The airflow temperature is generally not more than 50 ° C. The relative humidity of the airflow is generally not 80% dry.
6.Regularly change the activated carbon filter according to the specific use environment.
Filter replacement cycle
Early effect filter,
According to the degree of environmental cleanliness, the initial filter is usually 1-6 months.
In effect filter
Under the condition of rated air flow, it is necessary to replace the filter within 3-4 months, or when the resistance of the filter reaches more than 400 Pa, the filter must be replaced. If the filter uses a cleanable filter material, it is allowed to clean twice at most, that is to say, a new filter must be replaced.
High efficiency filters
If the primary filter is replaced once every 2-3 months, the service life of the high efficiency filter is usually more than 2 years.
Factory Production Picture
Contact Person: carol LI